The end coupling of internal installation for shielded single-conductor cables with plastic isolation. With tips under M12 bolt. Piece: piece
Number of cable cores: 1
Complete set: on the unarmored cable / with screw tips
Isolation type: plastic
Cable type: without armor
Coupling type: End
Allowable voltage: 10 kV
Section of the conductor: 25 mm ² / 35 mm ² / 50 mm ² / 70 mm ²
- Piece: piece
- Number of cable cores: 1
- Isolation type: plastic
- Coupling type: End
- Complete set: on the unarmored cable / with screw tips
- Cable type: without armor
- Allowable voltage: 10 kV
- Section of the conductor: 25 mm ² / 35 mm ² / 50 mm ² / 70 mm ²
Wire of the aluminum screen are cut off and without excesses connect special connectors to previously trained grounding conductors.
On the semiconducting screen the thermoseated tubes for protection against mechanical connectors are established. Conductors of grounding are pressed into the pressurizing mastic. Then the node of grounding is wrapped in copper tinned grid and is pressurized from above by the thermoseated tube.
The yellow tape for distribution of electric field strength is reeled up in the field of cut of the semiconducting screen of cable. On cutting the trekingostoyky tube on which internal surface the thermofusible pressurizing layer with function of alignment of electric field strength is put takes seat. The tube pressurizes the coupling from tip to grounding node. On couplings of outside installation insulating skirts in addition take seat.
Set with modification of L12 modification of L16 under M16 bolt, and modification of L20 under M20 bolt includes cable bolt terminals with opening under bolt of M12 and, respectively
In combination with the RICS adapter it is necessary to order modification of L16.
End couplings of internal installation with bolt tips.
Here end couplings for single-conductor cables with plastic isolation and the aluminum wire screen of 10, 20 and 35 kV are provided.
For example: APVKSV, PVKSP, APVKSP, PVKSP, APVPG, Apvp2g, PVP.