- Country of manufactureKazakhstan
Structure of system (standard complete set):
— a gas contamination signaling device on SZTs-1 methane;
— a gas contamination signaling device on SZTs-2 carbon monoxide;
— valve locking electromagnetic KZEG-ND;
— control unit of the BUS-1 alarm system;
— portable panel of control VPK-1;
— cable connecting BQ (ND) (BUS-1-klapan, 5 m);
— a cable connecting CC (a signaling device signaling device, 5 m) — 2 pieces;
— cable connecting BS (BUS-1-signalizator, 5 m.
By request the system can be completed with additional sensors of methane and carbon oxide, the valve on average pressure, the GSM transmitter, a cable for the control panel.
Purpose of SKZ "Crystal"-3. The system is intended for control:
- conditions of sensors of emergency parameters of a boiler room;
- conditions of sensors of emergency parameters of processing equipment;
- contents of natural gas and carbon oxide in air of controlled rooms;
- fire and security alarm system.
The system provides:
- overlapping of the pipeline of supply of gas the valve in an emergency;
- delivery of the sound and light alarm system with storing of a cause of accident and display of this information on the portable panel of control of VPK-1 or VPK-2 (in the presence);
- control of actuation mechanisms by means of a relay exit.
Scheme of connection of standard system
Use of system with the valve on 220B
Expansion of system
Functionality of the BUS-1 block