SEPARATORS OF THE CONTINUOUS PURGESP-0,15-0,3, SP-0,28-0,45, SP-0,7-0,6, SP-1,4-0,8, SP-1,5-0,8, SP-5,5-1,4.
Separators of a continuous and periodic purge are intended for division into steam and water of the steam-and-water mix which is formed of blowing-off water of boilers, condensate of steam receivers, a drainage of steam lines at decrease in its pressure to pressure in a separator with the subsequent use of heat of water and couple.
Separators can be applied in systems of collecting condensate for the purpose of reduction of a consumption of the consumed steam and losses of heat with the taken-away parokondensatny mix.
Device and principle of work of a separator of a continuous purge:
The separator represents a vertical cylindrical vessel of a welded design and consists of the case with the lower elliptic bottom welded on it; the top elliptic bottom connects to the case by means of the flange socket.
In a middle part of the case 2 or 4 support for installation of a separator in a hover on basic beams are welded.
In the lower part of the case there is an intake consisting of two kontsentrichno the installed feedwells and two tangentsialno branch pipes, vvarenny in the case, intended for reception tangentsialno of the brought blowing-off water.
In the top part of the case the separating device consisting of a set of specially unbent shovels and intended for separation of small drops of water from steam fastens bolts to a ring.
Work of a separator consists in reception of steam-and-water mix from a copper, its division into steam and water due to expansion and a rotary motion of a stream in a separator intake. In an intake there is an osaditelny operation. Finally steam osushivatsya in the separating device.